III. Process of Implementation:
- To replace the magnetic ballasts in all the FTL fittings with “Intelux” Active Power Factor Correcting (APFC) electronic ballasts (having constant light output for 150V-265V and low harmonics – THD<10%).
- We recommend “Intelux” 2x36W APFC ballasts tuned to 28W per lamp (56W total consumption) and use high lumen triphosphor lamps (“GE” Polylux) for 2x36W FTL fittings. Similarly, for 1x36W FTL fittings 28W tuned 1x36W APFC ballasts and Triphosphor lamps are suggested. For rest of the fittings, “Intelux” ballasts of regular (full) wattages and use of existing lamps is proposed.
- With the proposed lighting schemes the existing illumination (Lux) levels would be maintained.